Malta customer requires air conditioning and terminals for their starred hotel.
(1)Required chiller cooling capacity 500~530KW based on cold liquid outlet temperature-2degrees Celsius (2)Hanbell screw compressor dual system, refrigerant=R404, power supply=440V-3PH-60Hz
(1)Fruit processing room: 63 meters long, 16.4 meters wide and 3.71 meters high (2)The heat load is 430KW and the room temperature needs to be kept at 20 degrees
(1) Require condensing unit and evaporator for cold room to store beef and mutton (2) Room temperature around -18 degrees Celsius
(1) Need Bitzer compressor racks and its air cooling condenser; (2) Room temperature -27 degrees Celsius
(1) Need 5 units air cooling chillers, each unit capacity is 330KW (2) Chiller for central air condition use
Customer wants to adopt air cooled industrial chillers to cool down the prim ozone generators that they supply for ship owners. There are two types power supply, the voltage is 230V single phase, 50Hz and in larger systems in ships, it can variate from 380V-440V/3 phase 50/60Hz. Customer requires add a small transformer in 440V 3 phase systems into control board 220V. Circulating water to cool down ozone generators is fresh clean water, no corrosive to chiller system. All inbuilt chilled water pumps need enlarge to at least 30 meters lift. Customer also requires to control chiller on/off through remote by their PLC, and our chiller alarm signal can be output to their PLC controller.
Customer wants to adopt air conditioners plan for their pharmaceutical factory, target temperature 21±2 degree Celsius, target relative humidity is 40±2%, adjustable range from 35% to 50%, need 3 stages filters, with static pressure 500~600Pa, AHU cooling capacity is 8TR, 10TR and 14TR, with relevant air volume 5000, 6000 and 11000 cubic meters per hour, which will be installed in special pharmaceutical workshop areas, all compartments should have service doors & have necessary accessories for optimum performance.
(1) Need condensing unit and evaporator for 2 freezer room; (2) Room temperature -20 degrees Celsius (3) Room size: 30ft by 30ft by 10ft *1, 12ft by 12ft by 10ft*1 (4) Power supply and refrigerant: 220V-3phase-60HZ; R404a
Customer wants to adopt condensing units and air coolers/evaporator for their project <Ice Snow World Amusement Park>. The park occupies around 10,000 square meters, which adopts a fully enclosed steel structure with heat insulation. It should be kept indoor temperature -12℃~-18℃, to maintain the ice sculptures, such as different ice animals, ice CRH, ice slide, skating, etc. which are made of white ice, permeable ice and colorful ice.
(1)Cold water temperature request:10~15℃ (2)Cooling capacity:5KW and 58KW (3)Air cooling mode (4)Power supply:220V/380V-50HZ (5)Required RS485 interface
(1) Need compressor condensing unit and evaporator for the tunnel; (2) Required temperature can reach -40 degrees Celsius (3) Power supply and refrigerant: 400V-3phase-50HZ; R404a (4) Required cooling capacity: 22.5 kW at Temp. evaporation -40 ° C