Refrigeration Solutions For Peru Customer
Required cooling air for chicken meat cold chain inside cold room. Customer required cold room temperature keep 0~5℃, cold room size (L*W*H) 8*3.7*3 meters, there will be 2300 chickens entering into the cold room by chains, and will leave 20 minutes later, with chicken weight 2.4 kg per each, chicken temp. 38℃, and decreased to 20℃ when leaving the cold room.
Through evaluating and calculating, the required cooling capacity is about 112KW. Recommend Hanbell compressor and Bitzer compressor as option, make two plans for customer choosing:
(1)Chiller + Glycol evaporators (By water system)
Air cooled screw chiller, ESGA-55ISJTY, cooling capacity 124KW, cooling only, refrigerant R404A, power supply 220V/3PH/60HZ, chilled liquid inlet/outlet temp. 2/-5C, shell tube evaporator, finned tube condenser, micro-computer touch screen controller, propylene glycol 30%, equipped with glycol evaporators.
(2)Cold room refrigeration unit + air coolers (By refrigerant system)
Cold room condensing unit, ESGA-60NJBY, Bitzer semi-hermetic compressor, cooling capacity 111.7KW, cooling only, refrigerant R404A, power supply 220V/3PH/60HZ, room temp. 0~5C, evaporating temp. -7C, with condenser ES-CVT171.5, Danfoss expansion valve, equipped with air cooler EST33.6JT, double side air flow, room temp. Controller.
The Third Industrial Area, No. 150, Shasong Road, Bao'an District,Shenzhen, Guangdong, China.
Copyright © 2018 Shenzhen Eurostars Technology Co., Ltd. All Rights Reserved 粤ICP备18092071号 Powered by 300.cn SEO